CAN1-B149.1 and .2 codes.
Table 1 shows the units' gas orifice size for the elevations indicated.
* Each model has two burners. Each burner contains one of these orifices.
The millivolt appliances are manually controlled and feature a spark ignitor (piezo) that allows the appliance's pilot gas to be lit without the use of matches or batteries. This system will still function in the event of a power outage.
Do not use these appliances if any part has been under water. Immediately call a qualified, professional service technician to inspect the appliance and to replace any parts of the control system and any gas control which have been under water.
Ne pas se servir de cet appareil s'il a t plong dans l'eau, compltement ou en partie. Appeler un technicien qualifi pour inspecter l'appareil et remplacer toute partie du systme de contrle et toute commande qui ont t plongs dans l'eau.
This appliance may be installed in an aftermarket permanently located, manufactured home (USA only) or mobile home, where not prohibited by local codes. This appliance is only for use with the type of gas indicated on the rating plate. This appliance is not convertible for use with other gases, unless a certified kit is used.
Cet appareil peut tre install dans un maison prfabrique (.-U. seulement) ou mobile dj installe demeure si les rglements locaux le permettent. Cet appareil doit tre utilis uniquement avec les types de gaz indiqus sur la plaque signaltique. Ne pas l'utiliser avec d'autres gaz sauf si un kit de conversion certifi est install.
Test gage connections are provided on the front of the millivolt gas control valve (identified IN for the inlet and OUT for the manifold side). A ??" NPT test gage connection is provided at the inlet and outlet side of the electronic gas control valve.
Minimum inlet gas pressure to these appliances is 5.0 inches water column (1.24 kPa) for natural gas and 11.0 inches water column
(2.74 kPa) for propane for the purpose of input adjustment.
Maximum inlet gas supply pressure to these appliances is 10.5 inches water column (2.61 kPa) for natural gas and 13.0 inches water column (3.23 kPa) for propane.
These appliances must be isolated from the gas supply piping system (by closing their individual manual shut-off valve) during any pressure testing of the gas supply piping system at test pressures equal to or less than ?? psig (3.5 kPa).
These appliances and their individual shut-off valves must be disconnected from the gas supply piping system during any pressure testing of that system at pressures in excess of ?? psig (3.5 kPa).
These appliances must not be connected to a chimney or flue serving a separate solid fuel burning appliance.
Carbon Monoxide Poisoning: Early signs of carbon monoxide poisoning are similar to the flu with headaches, dizziness and/or nausea. If you have these signs, obtain fresh air immediately. Turn off the gas supply to the appliance and have it serviced by a qualified professional, as it may not be operating correctly.
NOTE: DIAGRAMS & ILLUSTRATIONS NOT TO SCALE.
WARNING: FAILURE TO COMPLY WITH
THE INSTALLATION AND OPERATING INSTRUCTIONS PROVIDED IN THIS DOCUMENT WILL RESULT IN AN IMPROPERLY INSTALLED AND OPERATING APPLIANCE, VOIDING ITS WARRANTY. ANY
CHANGE TO THIS APPLIANCE AND/OR
ITS OPERATING CONTROLS IS DANGEROUS. IMPROPER INSTALLATION OR USE
OF THIS APPLIANCE CAN CAUSE SERIOUS INJURY OR DEATH FROM FIRE,
BURNS, EXPLOSION OR CARBON MONOXIDE POISONING.
WARNING: CHILDREN AND ADULT